Experts spoke highly of PHINX for its unremitting efforts on popularization and application of energy efficiency heat pump products in central plains for the past years at Henan Heat Technology Annual Meeting.
Yes. The indoor heat pump on cooling will dehumidify and the resultant water needs to be led away. That is why they are typically mounted on an outside wall. If not, a condensate...
The technical terms of PHNIX hot water heat pump are based on the Department of Energy test procedure which is performed at an ambient room temperature of 15℃.
Leakage of refrigerant or a lack of refrigerant, please check the leaking point and vacuum again, charge the refrigerant with certain amount stated on the logo.
First, you have to consider installation and power supply. The PHNIX hot water heat pump requires 230V, 10amp electrical power to operate. Most natural gas or liquid petrol water heaters do not require electricity.
A ventilation system is designed to ventilate - introduce fresh air into an area. When the introduced air is colder than inside, they can use electric heaters to boost the temperature...
Please check if the main power supply is stable or not, at first because ELS means after transformer, the power supply is too low for CAREL controller ( its standard voltage is 24V and the min. is 20V);
Fuse break, power plug inserted loosely, no electricity in socket, no electricity or connecting wire in the unit loosens.
You can find the corresponding production manual in the technology information download center of the official website.
Please check the water system at first because FL means the water volume is not enough or the water system is jammed or the water pump is broken.