Experts spoke highly of PHINX for its unremitting efforts on popularization and application of energy efficiency heat pump products in central plains for the past years at Henan Heat Technology Annual Meeting.
Yes. The indoor heat pump on cooling will dehumidify and the resultant water needs to be led away. That is why they are typically mounted on an outside wall. If not, a condensate...
1) Check fan relay (if it's broken, change a new one); 2) Check fan capacitor (change a new one);
Please check the power source (lack of a phase or an error of phase). The compressor capacitor is broken down, change a new one. The compressor relay is broken down.
Fuse break, power plug inserted loosely, no electricity in socket, no electricity or connecting wire in the unit loosens.
You can find the corresponding production manual in the technology information download center of the official website.
Please check the water system at first because FL means the water volume is not enough or the water system is jammed or the water pump is broken.
Please check whether your set temperature is correct, your set temperature may be lower than your current water temperature.
You can solve the problem according to such points: 1) Check whether the filter is blocked; 2) Check whether the water flow rate is higher than the rated rate;
Please check the water inlet temperature sensor at first because E1 means this sensor is short or open; If necessary, please replace it with a new sensor.